dixell. DEFAULT SETTING VALUES. تا تا تست ه تا تن تا نا م ع. XR60C signals and records temperature alarms, together with their duration and max. View and Download Emerson Dixell XR60C installing and operating instructions online. Digital controller with defrost and fans management. Dixell XR60C. Dixell Srl reserves the right to change the composition of its products, even without or faulty operation send the instrument back to the distributor or to Dixell Srl.
|Published (Last):||19 January 2010|
|PDF File Size:||17.81 Mb|
|ePub File Size:||5.97 Mb|
|Price:||Free* [*Free Regsitration Required]|
Enter text from picture: The instrument shall not be used for purposes different from those described hereunder.
electronic controller DIXELL XR60C-0N1C0 378250
If the alarm LED is on, an alarm has taken place. To dicell the last temperature alarm happened; in programming mode it browses the. This function managed by the Fct parameter is designed to avoid short cycles of fans, that. The instrument must not be opened. Dizell and immediately release the SET key: Universal variable speed ac drive for induction and permanent magnetmotors pages.
Add to my manuals Add. In case of failure or faulty operation send the instrument back to the distributor or to “Dixell.
Don’t have an account? Flexible machine integration through communications 50 pages.
XR60C – AS Catering Supplies
Digital controller with defrost and fans management. This manual is part of the product and should be kept near the instrument for easy and quick.
An additional parameter “FSt” provides the setting of temperature, detected by the evaporator. Unidrive hs series; unidrive m series. Each LED function is described in the following table.
They have three relay outputs to control compressor, fan, and defrost, which can be. By pressing ‘print’ button you will print only current page.
After defrost, there is a timed fan delay allowing for drip time, set by means of the “Fnd”. To see the kind of alarm, the max min. The instrument is provided with screw terminal dixelll to connect cables with a cross section up nPS Pressure switch number: To confirm the operation, the “rSt” message starts blinking and the normal temperature. In case of applications cr60c industrial environments, the use of mains filters our mod.
XR60C signals and records temperature alarms, together with their duration and max value. This manual also for: Don’t show me this message again. On the display the following message is shown: Do not expose to water or moisture: Hold the SET key pressed for more than 3s, while eixell recorded alarm is displayed. Two defrost modes are available through the “tdF” parameter: Check the supply voltage is correct eixell connecting the instrument. Other parameters are used to control the.
Then the instrument displays the temperature once again. Push and immediately release the SET key or wait for 5 seconds to.
Dixell Srl reserves the right to change the composition of its products, even without notice. In case of fault in the thermostat probe the start and stop of the compressor are timed through.
To print dixel manual completely, please, download it.
EMERSON DIXELL XR60C INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
To display target set point; in programming mode it selects dixepl parameter or confirm an. Consider the maximum current which can be applied to each relay see Technical Data. Got it, continue to print. Ensure that the wires for probes, loads and the power supply are separated and far enough. The fan control mode is selected by means of the “FnC” parameter:. Page of 4 Go. The instrument is fully configurable. Comments to this Manuals Your Name. Fit the probe where it is not accessible by the End User.
This is used to make sure circulation of air only. At the end of defrost dripping time is started, its length is set in the FSt parameter.